We’ve covered fiber insertion loss in plenty of past blogs, so by now we hope that you know it’s the amount of signal loss that occurs as the signal travels along a cable link. We also hope you know that insertion loss is directly related to the length of the cable—the longer the cable, the greater the loss—and that any connection point along the way (connectors, splices, splitters, etc.) also adds to the loss.
Crônicas sobre cabeamento
Ganhe 3 CECs no nosso seminário pré-conferência BICSI sobre testes de conexões de fibra de alta velocidade
High speed applications are driving the deployment of multifiber MPO/MTP architectures in the data center, and it’s not just cloud and hyperscale data centers that are deploying these solutions. As the de facto interface for 40 Gig and 100 Gig switch-to-switch backbone data center applications that use parallel optics, MPO/MTP links are rapidly becoming commonplace in today’s enterprise data centers.
A passive optical LAN, also sometimes referred to as simply a passive optical network (PON), is a point-to-multipoint architecture that used passive optical splitters to split optical transmission signals from a single strand of singlemode fiber into multiple outputs. The technology has gained wide acceptance in outside plant applications, and it is now gaining traction in premise applications—especially in government and hospitality markets.
At this time of year, every industry tends to reflect on the past twelve months and make predictions about what 2018 will bring – it’s just what we do. So why should this year be any different?
In the spirit of the season and that “Sound of Music” favorite by Julie Andrews (that some have dubbed a holiday classic), we thought we’d take a moment to wish everyone Happy Holidays and Best Wishes for a Prosperous New Year and share with you a recap of some of this years’ favorite Cabling Chronicles (yes, it is sung to the tune of “My Favorite Things.”)
There’s no doubt that the European Union has a lot of rules and regulations—something frequently pointed out by those who campaigned for a Brexit vote in the United Kingdom. And many joke about some of the more ridiculous ones, like the law that prohibits people from eating pet horses, or the one that prohibits manufacturers of bottled water from labels suggesting that consumption could fight dehydration. (Since when didn’t water fight dehydration?)
A fusion splice is when two fibers are fused together using an electric arc. Often used with pigtails for connecting 250-micron outside plant fiber to 900-micron inside plant fiber at the building entrance, fusion splicing is achieved with a fusion splicing machine after the fiber is properly cleaved with a precision cleaver. Fusion splicing can be done for a single fiber or for 12-fiber ribbon cable via mass fusion splicing that splices all 12 fibers at once.
The much-anticipated higher levels of PoE have been quite the buzz in the industry. Now that the 802.3bt standard for PoE that includes Type 3 and Type 4 PoE is expected to be ratified early next year, we will start to see more devices forego their AC power connection for PoE.
I had a fun tech support call the other day that I think you will find interesting. A customer sent one of the ugliest traces we had seen in a while. “Help! What is going on here?” This came with the usual, it is urgent, his boss will kill him, the network is down, and he saw a dog and a cat making friendly on the way home from the job site.
Send us the trace file, better, please send it to us in the native, .flw, format. There is a lot of information in there that is very helpful to us, such as, what tester you are using, what firmware it has, and, what the failure is.
Fiber to the Desk (FTTD) applications have long been lumped in with other FTTX applications with the “X” signifying a variety of fiber optic access points, including Fiber to the Home (FTTH), Fiber to the Premise (FTTP), Fiber to the Curb (FTTC) and Fiber to the Building (FTTB). But it’s important to remember that FTTD is a premise application while many of the others are considered outside plant.